EATON 9355 MANUAL PDF
View and Download Eaton installation and operation manual online. 20/30 kva. UPS pdf manual download. CAUTION: REFER TO OPERATOR’S MANUAL – Refer to your operator’s manual for . Figure 1 shows the Eaton UPS UPS and an optional Extended. © Eaton Corporation. All Rights contained in this manual, but no liability can be accepted for any errors or omission. Figure 5 Powerware kVA and 40 kVA layout: 1:Graphical LCD; 2:XSlot-1; 3:XSlot-2; 4:Fans;. 5:Input.
|Published (Last):||12 February 2006|
|PDF File Size:||7.31 Mb|
|ePub File Size:||13.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
Don’t have an account? Page 8 Limited Factory Warranty Introduction This page intentionally left blank. Each UPS should be in Normal mode.
Floor Loading 8. Use the following troubleshooting chart to determine the UPS alarm condition. Turn the maintenance bypass switch to the UPS position to return to Normal mode. X-Slot cards allow the UPS to communicate in a variety of networking environments and with different types of devices. NOTE Check the battery recharge date on the packaging label. Page 48 Electrical Installation Figure Lift the door up and off the cabinet.
The load is now powered by utility power. Switch the bypass breaker to the ON position. Special Symbols Special Symbols The following are examples of symbols used on the UPS or accessories to alert you to important information: Never dispose of batteries in a fire. Press any button on the front panel display to activate the menu options. If the date has expired and the batteries were never recharged, do not use the UPS.
93555 more real power with optimal 0,9 output power factor reduces need to oversize. The load is now powered by utility power. Wiring Specifications And Diagrams Cabinet with an input manuak transformer, the input manuao is supplied by the input isolation transformer. Remove the two M10 bolts securing the stabilizing bracket to the pallet see Figure 2.
Page 16 Safety Warnings This page intentionally left blank. Consulte las normas locales para conocer los requisitos pertinentes.
EATON INSTALLATION AND OPERATION MANUAL Pdf Download.
If the optional input transformer is installed, an input neutral is not required. NOTE Conduit and wiring supplied by the customer. Initial Startup Disabled after initial startup Initial Startup Startup and operational checks must be performed 93355 an authorized Eaton Customer Service Engineer, or the warranty terms as specified on page 89 become void.
Usually mqnual alarms shown by the control panel do not mean that the output power is affected. Repeat Steps 11 through 13 for each cabinet. Introduction During brownouts, blackouts, and other power interruptions, batteries provide emergency power to safeguard operation.
Slowly roll the cabinet toward the rear of the pallet. Page 21 Remove the three M10 bolts securing the rear shipping pad to the pallet and remove the shipping pad see Figure 5.
Eaton 9355 Installation And Operation Manual
The UPS is now powering the load. Roll the cabinet to the desired location.
Got it, continue to print. It provides useful information about the UPS itself, load status, events, measurements, and settings see Figure Follow the instructions on the inside of the door to open or remove the front cover see Figure 28 and Figure Press the button to save the setting. Disabled after initial startup Initial Startup Startup and operational checks must be performed by an authorized Eaton Customer Service Engineer, or the warranty terms as specified on page 89 become void.
Page 46 Electrical Installation Figure DO NOT overtighten the screws; be sure to use the specified tightening torque values shown in Table 1. Page 28 see Figure Comments to this Manuals Your Name. Extended Battery Module Installation 6. Ups Maintenance Bypass Startup 3.
Control Terminals Normally Open Figure Parallel Communication This page intentionally left blank. If you have two Options Cabinets, remove the three circular knockouts on the left side of the first Options Cabinet.
Version 1 Bypass Breaker Rev D www. Page 86 Operation This page intentionally left blank. NOTE The input isolation transformer cannot be used with the wall-mounted bypass switch. Press and hold the button for three seconds, until the UPS stops beeping.